Runtime, or program which runs the application engineered by a programmer, executes the main activity of a PLC. It may be implemented on various hardware platforms. The platforms have different properties, such as processor computing power, operation memory and flash memory size, types and number of serial communication ports, integrated analog and digital inputs / outputs, etc. These properties determine the functionalities which a particular platform is able to support.
|PLC type||web - adwanced functions||web - basic functions
||BACnet server / client||SSCP over serial line||SSCP incoming connection||proxy support||Modbus serial server||minimum version of Domat IDE||maximum version of Domat IDE||currently on sale|
|w750-8101, wMX, wCIO
|w750-8102, wMX/COM, wCIO/COM||yes||yes||yes||see below||20||yes||yes (port x3)||188.8.131.52||-||yes|
Only incoming connections have a limit of 5 or 20, the number of outgoing connections is unlimited. So if I want to read data from 25 PLCs to one main PLC, this main PLC cannot be configured as the server and have 25 substations connected as clients. It is necessary to configure it in reverse. 25 servers and the main PLC will be their client (there will be 25 data sources in the program solution).
Only the serial port on the base unit (models w750-8102 and ... / COM) can be used for this function, and only in RS232 mode. To switch to the RS485 line, it is necessary to use an external serial converter of the RS232 interface to RS485, eg Domat R012. A standard serial modem cable DB9M - DB9F, connections 2-2, 3-3, 5-5, etc. is used to connect the converter to the controller. Additional cards of serial ports w750-652 for the function of serial SSCP communication (server or router) cannot be used.
Part of the memory is reserved for history data saving and their presentation over web interface. The web chart shows not only the currently trended data, but also history - values which have been sampled before the web browser opened the PLC web page. Data can be downloaded as a .csv file or image, and opened in a spreadsheet or imported into another program.
The web contains generic (i.e. with no need for extra engineering) page with records on appearance and changes of alarm states. The alarm history is important for maintenance and service - each event is provided with a time stamp, so the exact time of appearance, acknowledgement, and reset is available. The records can be downloaded as a .csv file.
Multiple users with different access rights can be defined at the web server, the user policy is configured in the same way as at the Domat Visual app or at the HT200 terminal. The web becomes „a small-scale SCADA“.
The web contains a generic page with system event records, such as PLC start, launching of processes, connection of users, etc. For diagnostics and service. All records can be downloaded as a .csv file.
The web server in a PLC is able to process data not only from the PLC it is running on, but also from other PLCs in the network. The system topology may be simplified.
It is not necessary to browse more PLCs to get data from the entire network. Data from different PLCs are communicated to a common web server, which is running on a single PLC in the network. All values can be displayed together in one panel or trend, the security policy may be simplified, etc.
Using the service web (generic web page) the basic network parameters can be configured, such as IP address, network mask, default gateway, and DNS server. This simplifies commissioning of PLCs with predefined applications. They do not need program upload, as the commissioning consists of configuring the network over web and of setting of control parameters and time schedulers. To change these parameters, Domat IDE is not necessary anymore.
A text template (same as for LCD menu definition) can be used as a web template, too. In this way, a PLC can be operated in the same way as if the user sets parameters directly over the LCD display in a PLC.
The on-line trends are sampling values as soon as the web page containig trends is opened in a browser. Data are not stored in the PLC, the trend is deleted if the browser window is closed. On-line trends help to diagnose the plant behaviour in time on a temporary basis.
BACnet is a standardized, manufacturer-independent communication protocol, developed for building control applications. A PLC may operate as a BACnet server, which provides data using BACnet / UDP protocol to clients, such as SCADA workstations. Variables which have to be mapped to BACnet objects automatically just need to be marked in Domat IDE. Eleven object types are supported: analog, binary and multistate inputs, outputs and values, as well as Schedule and Device objects.
BACnet client, on the contrary, integrates third-party systems into the Domat Runtime. Mostly, they are air handling and conditioning units, room controllers, etc. The third-party BACnet objects are mapped to Domat variables, and can be handled in the same way as other variables, such as those communicated from I/O modules.